Let me start by saying ‘awesome work’. I went with the wiser system as it works without internet, is from a ‘proper’ heating company and has individual room control.
I’ve had the system running (system 1, 1 thermostat, 5 trv’s) for a few months now using your binding.
I was getting constant disconnects since having it. So today I’ve done some testing and I’ve got to the root of the problem and now no disconnects.
The problem is as follows:
Drayton is set up for all rooms in my house.
I currently have 1 room left to add a trv into but this was added as a thing in the binding and the items setup ready.
This was the cause.
Although the Drayton app functions fine with the room, the binding errors out if there are NO devices present in that room.
Since removing the room from my thing file no more dropouts.
So don’t add rooms (things) for empty rooms. (Drayton app still has the room present)
Maybe this was the cause for some other users of the binding.
Been solid for 2 hours now. (Using the above, not the latest)